Swimming pools chemical make up, bather load, dirt mildew mold wind contaminates, location, pump run time, temperatures, size, determine ozone generator model. Heated swimming pools require 10 to 15 percent more ozone because it breaks down faster with higher temperatures.
Ozone Applications Information
Business, Home Ozone Applications
Perishable Food Applications
Ozone Book Information
Colon Cleansing Detoxification, Health Risks, Colonic Irrigation, Medical Ozone Therapy
Ozone Generators, Colon Cleansing Equipment, Pool and Spa Ozone Generators, Air Purifiers, Oxygen Generators
Other Home Business Products
Liquid Vitamin Mineral Dietary Supplement
Calculate Total Gallons Or Liters Based On Pool Size:
Length x Width x Depth x 7.481 = Total Gallons
Meters (L) x Meters (W) x Meters (D) = cubic meters x 1000 = Total Liters
Cubic Meters to Liters: Cubic Meters x 1000 = Total Liters
Commercial Swimming Pool 10 Percent Chlorine Dosage
Notes: Maximum gallons or Liters based on 24 hour pump run time. Use Sodium Bromide if additional chemicals are required. Dosage is 1kg (32 ounces) per 60,000 liters each 6 month period.
Domestic Home Swimming Pool 12 Hour Pump Run Time
Notes: Ideal pump run time is 12 hours, water circulating rate should be once each 3 to 4 hour period. The pump should re-circulate the total volume of pool water through the injector at least once each 4 hr period for maximum gallons. If the pool volume is say 10,000 gallons then the pump should be capable of re-circulating the water at the rate of at least 2500 gallon per hour. This way, the total volume of water through the pool will be pass through the injector at least once each 4 hour period. Less pump run time for the minimum gallons. Use Sodium Bromide if additional chemicals are required. Dosage is 1kg (32 ounces) per 60,000 liters each 6 month period.
Domestic Home Swimming Pool 24 Hour Pump Run Time
Less pump run time would be required for the minimum gallons. Use Sodium Bromide if additional chemicals are required. Dosage is 1kg (32 ounces) per 60,000 liters each 6 month period.
No Chlorine 12 Hour Pump Run Time
Important Additional Notes
1. Pump re-circulation rate of 1 x times the pool volume each 2 hours (maximum 3 hour) period is required.
2. 12 hour minimum run time is needed up to 80,000 liters thereafter 18 hours/day with increased run time for increased bather load.
3. For ozone only pools, keep ph above 8.2 and add flocculent monthly. Refer to your distributor for the recommended ozone compatible flocculent.
4. Larger pools may need proper ozone off gas venting and destruct system.
|Pool Size In Gallons||Pool Size In Liters||Ozone Generator|
|264 / 1,241||1000 / 4,700||200mg|
|1,320 / 3,169||5,000 / 12,000||500mg|
|3,433 / 6,338||13,000 / 24,000||1gr|
|6,602 / 11,884||25,000 / 45,000||2gr|
|13,205 / 25,089||50,000 / 95,000||4gr|
|26,410 / 36,974||100,000 / 140,000||6gr|
|38,294 / 50,179||145,000 / 190,000||8gr|
|51,499 / 62,063||195,000 / 235,000||10G|
|63,384 / 92,435||240,000 / 350,000||15G|
|95,076 / 124,127||360,000 / 470,000||20G|
|126,768 / 187,511||480,000 / 710,000||30G|
|190,152 / 253,536||720,000 / 960,000||40G|
|256,177 / 316,920||970,000 / 1,200,000||50G|
|330,125 / 369,740||1,250,000 / 1,400,000||60G|
|382,945 / 435,765||1,450,000 / 1,650,000||70G|
|448,970 / 501,790||1,700,000 / 1,900,000||80G|
|528,200 / 554,610||2,000,000 / 2,100,000||90G|
|581,020 / 633,840||2,200,000 / 2,400,000||100G|
Pool Ozone Machine Generator Management, Protocol, Theory